This steam condensing adds to the water in the pipe and naturally causes an overflow, which is led back to the boiler and re-used.
A boiler with horizontal sections is shown in fig.
7 he torque exerted on the driving-axle by the steam engine just at starting may be that due to the full boiler pressure acting in the cylinders, but usually the weight on the coupled wheels is hardly sufficient to enable advantage to be taken of the full boiler pressure, and it has to be throttled down by the regulator to prevent slipping.
In the ordinary working of a hot-water apparatus the expansion pipe already referred to will prevent any overdue pressure occurring in the boiler; should, however, the pipes Safety become blocked in any way while the apparatus is valves.
The second group consists of experiments made on a boiler belonging to the Great Eastern Railway Company.
From the boiler house are supplied with superheated steam at a pressure of 35 /b to the in.
It had a vertical boiler, and was carried on four wheels all coupled, the two cylinders being placed in an inclined position and having a bore of about 6 in.
The quality of the last is a matter of great importance; when it is unsuitable, the boilers will suffer, and the installation of a water-softening plant may save more in the expenses of boiler maintenance than it costs to operate.
- One pound of good Welsh coal properly burned in the fire-box of a locomotive yields about 15,000 British thermal units of heat at a temperature high enough to enable from 50 to 80% to flow across the boiler-heating surface to the water, the rest escaping up the chimney with the furnace gases.
This question of the standard engine of comparison, and the engine efficiency is considered in § 15 below, and the boiler efficiency in § It below.
It is not economical to force the boiler to work at too high a rate, because it has been practically demonstrated that the boiler efficiency decreases after a certain point, as the rate of combustion increases.
A few experimental results are set forth in Table XX., from which it will be seen that with a relatively low rate of combustion, a rate which denotes very light service, namely lb of coal per square foot of grate per hour, the efficiency of the boiler is %, which is as good a result as can be obtained with the best class of stationary boiler or marine boiler even when using economizers.
For large public buildings, factories, &c., heating by steam is generally adopted on account of the rapidity with which heat is available, and the great distance from the boiler at which warming is effected.
The one-pipe system is similar in principle, the pipe rising to its greatest height above the boiler and being then carried around as a single pipe falling all the while.
In small houses all requirements may be satisfied with a boiler heated by the kitchen fire.
For large buildings where large quantities of hot water are used an independent boiler of suitable size should be installed.
The flow pipe starts from the top of the boiler and is connected near the top of the cylinder, the return pipe joining the lower portions of the cylinder and boiler.
Should a defect occur with a wrought iron boiler it is usually necessary for the purpose of repair to disconnect and remove the whole apparatus, the heating system of which it forms a part being in the meantime useless.
To prevent this a safety valve should be fitted on the top of the boiler, or be connected thereto with a large pipe so as to be visible.
In the diaphragm valve a thin piece of metal is fixed to an outlet from the boiler, and when a moderate pressure is exceeded this gives way, allowing the water and steam to escape.
Fusible plugs are little used; they consist of pieces of softer metal inserted on the side of the boiler, which melt should the heat of the water rise above a certain temperature.
In districts where the water is of a " hard nature," that is, contains bicarbonate of lime in solution, the interior of the boiler cylinders, tanks and pipes of a hot water system will become incrusted with a deposit of lime which is gradually precipitated as the water is heated to boiling point.
In steam cranes much the same principle obtains in proportioning the boiler; e.g.
The Rocket possessed the three elements of efficiency of the modern locomotive - the internal water-surrounded fire-box and the multitubular flue in the boiler; the blast-pipe, by which the steam after doing its work in the cylinders was exhausted up the chimney, and thus served to increase the draught and promote the rapid combustion of the fuel; and the direct connexion of the steam cylinders, one on each side of the engine, with the two driving wheels mounted on one axle.
A second engine, the West Point, also built at West Point Foundry for the South Carolina railroad, differed from the Best Friend in having a horizontal boiler with 6 or 8 tubes, though in other respects it was similar.
The first group consists of experiments selected from the records of a large number made on the boiler of the locomotive belonging to the Purdue University, Indiana, U.S.A.
Cannock has tool, boiler, brick and tile works.
As the water is heated it becomes lighter, rises to the top of the boiler, and passes along the flow pipe.
From this point the " return " pipe drops, usually at the same rate as the flow pipe rises; and in due course the water reaches its starting point, the boiler, and is again heated and again circulated through the system.
5) a rising main is taken directly from the boiler to the topmost floor of the building, and from this branches are dropped to the lower floors, and connected by means of smaller branches to radiators or coils.
6) has many advantages, for it is safe, the boiler is small High and is easily managed, the temperature is well under control and may be regulated to suit the changing weather, and the small pipes present a neat appearance in a room.
The boiler consists of similar pipe coiled up to form a fire-box, inside which the furnace is lighted.
Every installation is made up of a boiler or other water heater, a tank or cylinder to contain the water when heated, and a cistern of cold water, the supply from which to the system is regulated automatically by a ball valve.
All draw off services are taken off from the flow pipe which connects the boiler with the tank.
In the choice of a boiler of this description it should be remembered that rapid heating, economical combustion of fuel, and facilities for cleaning, are requisites, the absence of any of which considerably lowers the efficiency of the apparatus.
With " very hard " water this deposit may require removal every three months; in London it is usual to clean out the boiler every six months and the cylinders and tanks at longer intervals.
The lime deposit or " fur " is a poor conductor of heat, and it is therefore most detrimental to the efficiency of the system to allow the interior of the boiler or any other portion to become furred up. Further, if not removed, the fur will in a short time bring about a fracture in the boiler.
Boiler is so placed as also to form part of the counterbalance.
The first one of the group was made on the boiler fixed in the locomotive yard at Stratford, and the two remaining experiments of the group were made while the engine was working a train between London and March.
18), the blast-pipe orifice B is placed at about the centre of the boiler barrel, and the exhaust steam is discharged straight into the trumpet-shaped end of the chimney, which is continued down inside the smoke-box.
V hen the train is started and is moving slowly, the toroue acting on the driving-axle may be estimated as that due to about 85°/, of the full boiler pressure acting in the cylinders.
Hence, if p is the maximum value of the mean effective pressure corresponding to about 85% of the boiler pressure,, uW = pd 2 le /D (26) is an expression giving a relation between the total weight on the coupled wheels, their diameters and the size of the cylinder.
Let the boiler pressure be 175 lb per square inch.
Among later additions were gunmounting stores, boiler shop, boat sheds, canteen, coal stores, &c., together with a double dock 750 ft.
Boiler Tap to, empty +G the same water is used over and over again, and no fresh deposit of fur occurs.
„ regulating a s Boiler Tap to.
The supply from the cold water cistern enters the bottom of the cylinder, and thence travels by way of the return pipe to the boiler, where it is heated, and back through the flow pipe to the cylinder, which is thus soon filled with hot water.
12 the cylinder is placed in proximity to the boiler; this is the usual and most effective method, but it may be placed some distance away if desired.
A suitable proportion between the size of the tank or cylinder and that of the boiler is 8 or io to 1.
The shape mostly used is the " saddle " boiler, or some variation upon this very old pattern.
A notable feature of modern boiler construction is the mode of building the apparatus of cast iron in either horizontal or vertical sections.
The size of the boiler may be increased or diminished by the addition or subtraction of one or more sections; these, being simple in design, are easily fitted together, and should a section become defective it is a simple matter to insert a new one in its place.
This high mean pressure cannot be maintained for long, because as the speed increases the demand for steam per unit of time increases, so that cut-off must take place earlier and earlier in the stroke, the limiting steady speed being attained when the rate at which steam is supplied to the cylinders is adjusted by the cut-off to be equal to the maximum rate at which the boiler can produce steam, which depends upon the maximum rate at which coal can be burnt per square foot of grate.
Combined Engine and Boiler Efficiency.
The boiler evaporated 184 cub.